V-bank box type HEPA filters use sub-micron glass fibers formed into a high-density paper.
Glass filament separators are used to form the media into mini-pleat panels that withstand high-velocity airflow.
Mini-pleat packs are sealed to the frame with two-component polyurethane to increase rigidity and prevent bypass leakage.
|Efficiency EN1822@ MPPS [%]||>95 %||>99,95 %||>99,995 %|
|Initial-ΔP[Pa]at nominal airflow||125||220||250|
|Rec. final pressure drop [Pa]||600||600||600|
|Max. temp. [°C]||80°||80°||80°|
(E=efficiency N=V quantity)
|VS592592292-E (E11-H14) N5||592||592||292||3400||5|
|VS592592292-E (E11-H14) N4||490||592||292||2800||4|
|VS287592292-E (E11-H14) N4||287||592||292||1700||4|
Please turn to the air filters page to know more equipment.
We have rich experience in the establishment of clean rooms. We have built suitable clean environments for many companies. If you have other questions about clean rooms, please contact us immediately to obtain solutions.
The email will be sent directly to our CEO Ivy Wang and we will respond to your inquiry within 12 hours.